We have a lot of pole mounted meters with 200amp panels.They have feedthru lugs to feed the mobile home and 4 or 8 circuit breakers slots. Most of these panels feed the customers well pumps.What are some thoughts on taping the load side of S. E. rated transfer switch to feed a whether proof sub panel.
Thinking of clear taps or bugs.Short nipple out the back of the TS into a WP sub panel for well. We are still using the 2005 NEC
You can per 240.92 (D) (1-5) (2008 NEC)