Model #: 30kw
Serial #: 3005221291
Total run hours: 6
Fuel source: NG or LP: LP
Length of fuel run: ?
Diameter of fuel pipe: 3/4" copper
Last maintenance date: July 8, 2020
Last valve adjustment date: NA
Last battery replacement date: NA
Error Code: NONE
This is a recent install, we did not do it. Customer said it is hard to start, takes several attempts to get started but starts. When I arrived, it would not start. The fuel solenoid was stick, gas pressure at 14iwc. Disassembled solenoid and put back together. Dropped pressure to 10iwc. Started fine. Controller was set to Natural gas, I changed it to LP. Installer said they changed the orifice in the demand regulator to the smaller one. Unit ran but was blackening the exhaust vent on the unit. I cleaned the unit up and it seemed fine. Now the unit is still blacking the vent and took several attempts to get started. Have you guys had one with these problems.?