You could have destroyed the regulator in the generator cabinet.
Could have damaged the diaphragm in the fuel regulator. Install a manometer in port 2 to verify gas is not bleeding through when the unit is off. Was it natural gas or high pressure propane?
Edit-......Skip beat me to it.
Agree with both. Why was a secondary regulator not installed when the gas line was ran?